17kv Polymer High Voltage Surge Arresters Drice Gapless Lightning
|TYPE||Rated Voltage KV(rms)||Continuous operation voltage KV (crest)||Steep current impulse kv (creset)||1mA DC reference voltage in not less than||Lightning impulse current residual pressure of not more than||2ms Square wave current A||Flexural strength N|
The new device has a composite MOA with pillars function,surge
arrester function,power function,examine the electrical gronding
function of the four function together as a whole,has the form of a
multi-purpose sturcture.Adopt this such devices can be reduced
while a lightning cross arm;reduce sagging wire fixing three
insulators;that is to reduce the sevenpeeling point,reduce
construction wor,while reducing the six points of failure,it is
able to simplify wiring devices,further increasing operational
safety and reliability purpose,the line is more simple and
beautiful.Furthermore,this device intergrates a variety of
funcitonsthe need seven pointsof the original insulation stripping
and insulation in one place,and the insulating cover design is
reasonable,can truly full insulation,creating favorable condictions
for the safe operation and charged.
The product characteristic:
1.Arrester core and jacket,by molding,making it non-dense whole
cavity,eliminating moisture absorption caused by respiration,to
prevent accidents caused by lightning chip damp fundamentally.
2.The surge arrester with a special internal reinforcement
structure,it has a good mechanical function,can seve as insulators.
3.Arrester synthetic jacket with silicone rubber material to the
anti-filthy strong performance and good proof performance,in
additon,light weight,long life.
4.Arrester are III class heavy contamination by resistance design
and production,and the insulation jacket minimum creepage distance
of 31m/kv,creepage distance of 372mm.
5.Arrester overall structure optimized design,with a comvination of
a.Both ground stms meet electrical inspection,the ground needs to
simplify the tower unit.
b.A special reinforcing structure,it has good mechanical
properties,can doublepost insulators.
c.The connection terminal blocks can be segmented cable
fault,reduce the power range,with a knife breaking features.
d.The arrester with full insulation design,can effectively prevent
external damage and other accidents.
1.Before installation,the arresters shall be stored in clean and
dry rooms and kept away form the corrosions by corrosive gas or
2.Before put into operation,preventative testing shall be made on
the arrester.And after the arrester has been put into
operation,regular testing shall be made as follows and follows and
comparison shall be made with the data before the operation
according to the attached table.(Every 5 years for arrester of 10kV
or under,and every 2 year for arrester of 35kV and above)
a.Measure the insulation resistance of the arrester;
b.Measure the reference voltage of the arrester under direct
current of 1mA
c.Meausre the leak age current under the reference voltage of 0.75
time direct current of 1mA
1. Distribution networks
2. Transmission line
4. Railway power station
5. Alternator and electromotor